Payment & Shipping Terms:
|Application:||Personal Computers , Network , Telecom||Rated Frequency:||50/60HZ|
|Production Place:||ShenZhen GuangDong China||Package:||Carton, Export Type Packing|
Outdoor Telecom Solar Panel Power System 1KVA - 10KVA 50HZ / 60HZ
1. Pure sine wave inverter
2. Built-in MPPT solar charge controller
3. Could be built-in battery
4. Protection degree:IP55
5. Configurable input voltage range for home appliances computers via LCD setting and personal
6. Configurable AC/Solar Charger priority via LCD setting
7. Compatible to mains voltage or generator power
8. Auto restart while AC is recovering
9. Overload/Over temperature/short circuit protection
10. Configurable battery charging current based on applications via LCD setting
Fine dust-proof, water-proof features
According to the overall standard of design dust-proof a n d water-proofIP55
1. With a sun protection,heat insulation,roof ventilation
2. With waterproof and the filtration dust inlet; the cabinet front door shutters with w a terproof design, on the back of welding water tank, water tank installed above the net with quick release feature of the dust .
Product Descriptions of Solar Inverter
|Input wave form||Sine wave (utility or generator)|
|Normal voltage||120VAC(option) 230VAC|
|Low voltage re trip||90V±4% & 184V/154V±4%|
|Low voltage re engage||100V±4% & 194V/164V±4%|
|High voltage re trip||140V±4% & 253V±4%|
|High voltage re engage||135V±4% & 243V±4%|
|Normal input frequency||50Hz/ 60Hz (auto detection)|
|Output Wave form||(Bypass mode)same as input|
|Over-Load Protection||Circuit breaker|
|Short circuit Protection||Circuit breaker|
|Efficiency on line transfer mode||undefined95%|
|Line transfer time||10ms Typical|
|Bypass without battery connected||Yes|
|Output wave form||Pure sine wave|
|Output continuos power watts||1000||1500||2000||3000||4000||5000||6000||8000||10000|
|Nominal Output Voltage rms||120VAC(option) 230VAC|
|Output Voltage regulation||+/- 10%rms|
|Output frequency||50Hz ± 0.3Hz or 60Hz ± 0.3Hz|
|Short circuit protection||Yes,fault after 1 secs|
|Nominal input voltage||24V/48V||48V|
|Minimum start voltage||20V/40V||40V|
|Low battery alarm||21V/42V||42V|
|Low battery trip||20V/40V||40V|
|High voltage alarm||32V/64V||64V|
|Output voltage||Dependent on battery type|
|Charge current||10-85A MAX||70A||85A|
|Battery initial voltage for start up||0-15.7v for 12v(*2 for 24v;*4 for 48v)|
|Over charge protection||15.7v for 12v(*2 for 24v;*4 for 48v)|
|MPPT Range@Operating Voltage||30-115VDC/60-115VDC|
|Maximum PV Array Open Circuit Voltage||145VDC|
|Maximum Charging Current||60A|
|APPLICATION OF OUR PRODUCT|
1. Living house and home building
2. Office building, factory and warehouse
3. Shopping mall, stadium and so on
4. Power station, field operation and some huge engineer construction
5. suitable for various home appliance, Office equipment,Journeys, Camping, Tents, Boat Trip
Introduction of Company
Shenzhen SORO Electronics Co., Ltd is a professional UPS and inverter manufacturer in the field of power electronics for 13 years. We have two large production UPS sites, Zhejiang and Shenzhen. We have own our SMT department. SORO UPS has been a leading enterprise in the UPS industry in China.
Since established, The company has carried out three strategies: operation innovation strategy, people-oriented strategy , technical guidance strategy, and implemented strict scientific management with full-fledged quality management system. The company invests 10% of its annual revenue in researching and development every year. We had international advanced equipments for developing , testing and producing. SORO UPS invited the best technical elites at home, meanwhile, the company established perfect cooperation relationship with domestic scientific research units and academies, to strive for making products that reach advanced world standards.
|WHY CHOOSE US ?|
1, QC Control
The company ranks first in passing the ISO9001 international quality system certification.We established a complete quality system ranging from material source, process, assembling to testing. Most of our products have been certified to meet international safety standards, such as CE (LVD/EMC), CUL,FCC.
2, Best Partner
We have co-operative partner throughout the world including USA, Europe, South America, South Africa, Middle Eastern, India, Turkey, Pakistan, Iran and so on .We offer wide range quality products either from our own standard range or customer-made to your specifications. SORO is becoming the most growthful China UPS supplier all over the world.
1. How to choose suitable inverter?
If your load is resistive loads, such as: bulbs, you can choose a modified wave inverter. But if it is inductive loads and capacitive loads, we recommend using pure sine wave power inverter.
For example: fans, precision instruments, air conditioner, fridge, coffee machine, computer, and so on.
Modified wave can be started with some inductive loads, but effect for load using life,because capacitive loads and inductive loads need high quality power.
2. How do I choose the size of the inverter?
Different types of load demand for power are different. You can view the load power values to determine the
size of the power inverter.
Resistive load: you can choose the same power as the load.
Capacitive loads: according to the load, you can choose 2-5 times power.
Inductive loads: according to the load, you can choose 4-7 times power.
3. How connection between batteries and an power inverter?
We usually believe that cables connecting battery terminal to inverter shorter is better. If you are just standard cable should be less than 0.5M, but should correspond to the polarity of the batteries and inverter-side outside. If you want to lengthen the distance between battery and inverter, please contact us and we will calculate the recommended cable size and length. Due to long distances using a cable connection, there will be a reduced voltage, which means that the inverter voltage would be far below the battery terminal voltage, this inverter will appear under voltage alarm conditions.
4. How to calculate the load of working hours requires configuration of the battery size?
We will usually have a formula to calculate, but it is not hundred percent accurate, because there is also the battery's condition, the old batteries have some loss,so this is only a reference value:
Work hours = battery capacity * battery voltage * 0.8/load power (H= AH*V*0.8/W)